Village Plumbing and Heating, was in Van Nuys this morning. We were schdeuled to to do a leak detection on a main line at a service station. We went out and got approved to do work, and in the middle of digging the owner called saying he didnt want to pay the price that was quoted to him. So we stopped working backed
filled the earth that was removed and went to next customer.. Village Plumbing and Heating was in Woodland Hills. Long time customer needed a irrigation line to be repaired. Village Plumbing and Heating went out dug up location of irrigation line. Removed bad section of pipe, replaced with new. Replaced earth in ground. Tested no leaks.
Tags: back-filled earth van nuys, back-filled earth woodland hills, dug up earth woodland hills, irrigation line van nuys, irrigation line woodland hills, leak detection van nuys, lek detection van nuys, main line stoppage van nuys, no leaks woodland hills, removed bad section of pipe van nuys, removed bad section of pipe woodland hills, replaced with new pipe van nuys, replaced with new pipe woodland hills, test no leaks van nuys, test no leaks woodland hills, van nuys back filled earth, van nuys irrigation line, Van Nuys Leak Detection, van nuys leak detectiuon, Van Nuys lkeak detection, van nuys main line stoppage, van nuys re moved bad section of pipe, van nuys replaced with new pipe, van nuys test no leaks, woodland hills back-filled earth, woodland hills dug up earth, woodland hills irrigation line, woodland hills no leaks, woodland hills removed bad section of pipe, woodland hills replaced with new pipe, woodland hills test no leaks